Whether you have a hot tub, commercial spa, or an inflatable hot tub, ensuring the highest water quality is essential. Like swimming pools, strict regimes around water testing are required for your spa.
Spas are becoming increasingly popular in the domestic and commercial market as a cheaper alternative to swimming pools, providing relaxation and medical benefits to users. With the increased risk around infectious diseases in spas, it is crucial that a strict testing and monitoring regime is in place. Like pools, the frequency of water testing will be flexible depending on the usage and location of the spa. Increased bather load will require more frequent testing. Your operating procedure will include daily, monthly and/or quarterly actions to ensure the highest water quality.
As always, regulations vary by country, region and sometimes system. In the UK, new guidelines HSG282 have been released to help the control of legionella and other infectious agents in spa-pool systems. The minimum key parameters under HSG282 in which you should test for:
When testing your spa-pool, you need to take samples at three different times to ensure good water quality. The first is when the jet functions are not in operation, and the second when they are. The final sample should be taken after the maximum use of the spa. The water chemistry will be affected by the jet systems and by bather load.
As mentioned above, the minimum key parameters under HSG 282 in which you should test for are pH, disinfection (e.g. chlorine, bromine) and total dissolved solids (TDS). Whilst these tests are the minimum, further parameters should be included in your testing regime to ensure effective water quality monitoring:
In Table 1 we have summarised the key testing parameters, including the target range which you should be achieving for each test parameter. These are based on industry guidelines, but we would always recommend you check your local regulations to ensure full compliance.
|Bromine||Very favourable in spa disinfection as it is more effective at higher temperatures.||4.0 – 6.0 mg/L|
|Free Chlorine||Free chlorine is a measure of the most active disinfectant.||3.0 – 5.0 mg/L|
|Combined Chlorine||Measure of chlorine that has been used up during the disinfection process.||0 – 1.0 mg/L|
|pH||The measure of how acidic or alkaline the water is, this influences efficiency of the disinfectant.||7.0 – 7.6 pH units|
|Total Dissolved Solids||Measure of dissolved organic and inorganic substances in the water.||No more than 1,000 mg/L|
|Total Alkalinity||Alkalinity protects the water from changes in pH.||80 – 200 mg/L CaCO3|
|Cyanuric Acid||Protects chlorine ions from degradation by UV light. This may be used for outdoor spas.||Below 200 mg/L|
|Calcium Hardness||Measure of whether the water is scaling or corrosive.||80 – 200 mg/L|
|Ozone||Some spas will have ozone generators, which provides a secondary disinfection and effectively kills infectious diseases and means you can have lower levels of disinfectant.||1.2 – 1.5 mg/L O3|
|Phosphate||Naturally present in water and is a key nutrient for algae growth.||Below 0.01 mg/L|
|Turbidity||Measure of how cloudy the water is. This can indicate key problems in filter media, poor water chemistry and other issues in spa maintenance.||Below 0.5 NTU|
In addition to the key testing parameters already outlined, it is recommended you do a full screen of microbiological contaminants through an accredited water testing laboratory. Performed on a monthly basis, the following tests should be completed:
To get the most accurate picture of your microbiological contaminants, the sample should be taken when the spa is at its maximise usage, or immediately afterwards.
There is a wide range of testing methods to monitor your water quality and the required solution is dependent on the use of the spa facility. For domestic use, where the use of the spa is sporadic and limited to a small number of users, a basic test kit could be used. For commercial settings where the spa facilities are used by multiple individuals, a digital test solution is required. A digital solution will provide you with the most accurate results for the critical water quality parameters, giving a much clearer picture of your overall water quality.
To comply with HSG 282 guidelines, a photometer can be used for disinfection and pH monitoring, with an electrochemical sensor used for TDS monitoring.
Palintest’s Lumiso Pooltest 4 photometer has been specifically designed for testing spas and indoor pools, covering the key water quality parameters; Total & Free Chlorine, Bromine, pH and Total Alkalinity. This should be used in conjunction with our electrochemical TDS meter, for TDS and temperature measurement, giving you complete compliance to HSG 282.
For more information around our Palintest offerings for your spa maintenance, contact our team.
To ensure that you are operating your hot tub or spa in a safe manner, you should consider the following guidelines:
Whilst not a requirement, it is suggested that all spa facilities, including those for personal use, follow the guidelines of HSG 282 to ensure safe bathing.
For more information about spa testing, download our spa chemistry guide, containing all the information you need for effective management of spa facilities.
6th March 2023
Palintest exists with a simple but crucial purpose; to safeguard water for everyone, every day. It is this purpose that guides us in all we do. After an extensive review and realignment to this purpose, Palintest has decided to withdraw our soil testing range of products from the market. Our Soil Test range has enjoyed many years of success and we are proud of the positive impact it has had on agricultural communities globally. However, in order to focus on our core water analysis technologies, our Soil Test range will be retired.
23rd February 2023
Lead exposure, through the contamination of drinking water, can have major health implications. It is vital that municipal authorities can employ accurate testing methods to identify sources of lead contamination. Multiple techniques including Inductively Coupled Plasma Mass Spectrometry (ICP/MS) and Anodic Stripping Voltammetry (ASV) can be used to detect lead in water – in this article we review these methods in more detail.
8th February 2023
The human body needs small quantities of copper to function. But as well as being a nutrient, copper can also be harmful if consumed in large quantities. Palintest’s patented single use copper sensor, which can be used in our Kemio™ product range, can allow water utilities organisations to easily carry out testing for copper in-situ at consumers’ taps.